The transmitter can monitor a maximum of 100 Amps.
- Single-phase 100 Amp power supply - use one transmitter and one CT Clamp.
- Three-phase 100 Amp power supply - use one transmitter and three CT Clamps.
- Three-phase 300 Amp power supply - use three transmitters, each with their own CT Clamp. This means you will see each phase on a separate channel on the energy monitor